2005/67: Sanitary fixtures in a weight loss and fitness centre
- Valid from
- Information provider
- Ministry of Business, Innovation and Employment
- Information type
This determination considered whether, without a shower, the fitness centre complied with clause G1 Personal Hygiene of the Building Code as nearly as was reasonably practicable.