2019/013: Regarding the refusal to issue a code compliance certificate for the relocation of and 18-year-old alterations to a house
- Valid from
- Information provider
- Ministry of Business, Innovation and Employment
- Information type
This determination considers the compliance of consented work for the relocation of an existing building onto a new site and alterations to the building. The authority refused to issue the code compliance certificate for the work because of concerns over the performance of a membrane roof to a new extension built as part of the relocation consent.